188.8.131.52 One of the two SCBAs present shall be in the
CGA P-1, 184.108.40.206
possession of a qualified backup person present at the
scene when the SCBAs are being used.
4.3 Flammable and Combustible Liquids
4.3.1 Aisles in areas that qualify as indoor liquid storage areas as per
NFPA 30, 220.127.116.11;
NFPA 30, "Flammable and Combustible Liquids Code", shall
NFPA 30, 18.104.22.168;
be 4 ft wide. Aisles in other flammable liquid storage areas
shall be 6 ft wide.
22.214.171.124 Aisles at least 3 ft wide shall be provided where
necessary to allow for access to doors, windows, or
4.3.2 Class I flammable liquids (see definition) shall not be stored in
NFPA 30, 126.96.36.199;
basement areas. Class II and Class IIIA combustible liquids
NFPA 30, 4.5.14;
(see definition) shall not be stored in basement areas unless
NFPA 30, 188.8.131.52
those areas are protected with automatic sprinkler systems.
4.3.3 Class I flammable liquids shall not be stored such that a fire in
NFPA 30, 184.108.40.206
the liquid storage area would prevent egress from the area.
4.3.4 In general purpose warehouses, flammable and combustible
NFPA 30, 4.5.28.(a)
liquids shall not be stored in the same pile or on the same rack as
220.127.116.11 Ordinary combustibles, other than those used for
NFPA 30, 18.104.22.168;
packaging flammable liquids, shall be stored a minimum
NFPA 30, 22.214.171.124;
of 8 ft from flammable or combustible liquids.
NFPA 30, 126.96.36.199.(b)
188.8.131.52 Where flammable liquids are packaged together with
NFPA 30, 184.108.40.206.(a)
ordinary combustibles, such as in kits, storage shall be
considered on the basis of whichever commodity
4.3.5 Storage of empty or idle pallets inside a flammable liquid storage
NFPA 30, 220.127.116.11
area shall not exceed 2,500 ft.2 and 6 ft. in height.
4.3.6 Containers in piles shall be stacked in such a manner as to
NFPA 30, 4.-4.3.8;
provide stability and to prevent excess stress on container walls.