126.96.36.199 The maximum amount of Class I, II, and IIIA
NFPA 45, 188.8.131.52
flammable and combustible liquids that can be stored in
a laboratory fire area is 400 gallons of which the
maximum amount of Class I flammable liquids is 300
4.3.16 Sites for outdoor storage lockers (see definition) shall be
NFPA 30, 4.6.4
reviewed to ensure proper placement, separation, etc.
184.108.40.206 Multiple outdoor storage lockers at a given site shall be
NFPA 30, 4.6.4
separated according to requirements in NFPA 30.
220.127.116.11 In outdoor storage lockers, containers in their original
NFPA 30, 18.104.22.168.1
shipping packages shall be permitted to be stored either
on pallets or in piles, while unpacked containers shall
be stored on shelves or on the floor.
22.214.171.124 No other flammable or combustible materials shall be
NFPA 30, 126.96.36.199.2
stored at designated outdoor storage locker sites.
188.8.131.52 Outdoor storage lockers shall be placarded according to
NFPA 30, 184.108.40.206.3;
[NOTE: Additional requirements can be found in NFPA 430, "Code for
Storage of Solid and Liquid Oxidizers", when quantities exceed 4,000
pounds of Class 1 oxidizer (see definition), 1,000 pounds of Class 2
Oxidizer (see definition), 200 pounds of Class 3 Oxidizer (see
definition), or 10 pounds of Class 4 Oxidizer (see definition). Oxidizer
classes are defined in NFPA 430".]
4.4.1 Oxidizer storage areas shall be conspicuously identified with the
NFPA 430, 2.2.1
words "Class (appropriate classification number) Oxidizers."
220.127.116.11 Areas used to store oxidizers of different classes shall be
NFPA 430, 2.2.2
marked as containing the most severe hazard.
Water based manual fire fighting equipment shall be used in
NFPA 430, 2.11.6
Oxidizer storage areas and flammable liquids storage areas require water- based fire suppression systems. While
there are no requirements to keep water reactive materials away from oxidizers, when storing oxidizers,
consideration should be given to the additional hazard posed by the presence of water reactive materials when water
suppression systems are activated.