e. [Racks] [Cabinets] and anchorage shall be seismic rated as indicated in
Terminals and connectors.
a. Connectors shall meet the requirements of UL 486A or comparable standard
by any nationally recognized testing laboratory (NRTL) recognized under
29 CFR 1910.7.
b. Clearly mark each cell post for permanent identification of polarity, and seal
to the cover.
Select 15-minute rating for UPS applications, 3-hour for general-purpose.
c. Provide [lead-plated copper bus bar] [
] connectors for connecting
the jars in series. All connecting [bus] [straps] and hardware shall be able to
] rating of the battery, or a continuous
carry the [15-minute] [3-hour] [
current equal to the battery's end-of-discharge voltage of [1.75 V] [
cell, whichever provides the higher current-carrying capability. This shall be
accomplished without exceeding a temperature rise of 30C above ambient.
Provide insulated cable connectors between [tiers] [steps] and between jars
on different [rack] [cabinet] sections where the sections are located adjacent
to each other, or back-to-back. Arrange cable on the [racks] [cabinets] to
prevent external mechanical damage. Provide details of copper terminal
connectors that are completely lead-plated.
Coodinate the selection of agent in the following paragraph with the scope of work specified in paragraphs 1.2 and
d. The [Owner will] [Seller shall] provide the cable interconnections between the
battery string (positive and negative terminals) and the battery charger. The
[Owner will] [Seller shall] also provide the inter-rack and inter-tier cabling
where rack sections are not arranged end-to-end or back-to-back. Provide
[2-hole] [4-hole] [ -hole] compression-type lead-plated connectors sized to
accommodate [Owner] [Seller] cables in sizes specified below. Provide
multi-cable terminal connections for each connection.
Privacy Statement - Press Release - Copyright Information. - Contact Us